Fire Alarm -- Description
Class B Wiring is meant to make sure that the wires are always connected to all the devices on the loop outside of the panel.
What is Conventional Fire Alarm Class B Wiring?
By Douglas Krantz
people are paranoid. They're afraid everything is working against them. They're in fear that that if anything goes wrong, like a wire breaks or a connection comes loose, lives will be lost, or property will be destroyed, or both.
Wiring, for example, is considered to be unreliable. Even when installed perfectly -- it's in conduit and all connections are properly made -- wiring can be damaged by external forces: a smoke detector
is broken by a forklift, a mini-horn is disconnected in an apartment so the resident doesn't have to listen to it, a connection is corroded by water leaking from the roof, etc.
This of course doesn't include poorly made connections, squirrels chewing on the wire (I've seen that), other vendors removing the fire alarm wire by mistake, and anything else that breaks the wire.
Keeping the Fire Alarm System Working
A broken wire or connection keeps the fire alarm system
from working: detectors don't detect, fire horns don't sound the alarm, strobes don't flash.
That is why fire marshals and other Authorities Having Jurisdiction (AHJ) want any problems fixed early; once a fire starts, it's too late to troubleshoot and fix the fire alarm system.
To make sure the wire throughout the building is always working, the wire is supervised
, or continually checked for continuity, by the fire alarm control panel using a small electrical current.
The current, as it leaves the panel, goes out one of a pair of wires, goes through a current limiting resistor called an End-of-Line resistor (EOL)
, and returns on the other wire. This pair, along with the EOL, makes up a fire alarm loop. Devices are connected to this loop so their connections, also, receive the supervision current
If this current stops for any reason, the supervision circuitry in the fire alarm panel assumes that the whole loop is not working, and calls out a trouble condition. The trouble condition on the panel, of course, cannot be reset; the cause of the trouble can only be fixed.
Besides the devices themselves being connected, there are no "T" taps; no wire runs to another device not supervised by this loop. This includes short runs within a box that doesn't run the supervision wire through any devices on the loop.
Class B Wiring
Class A Loops
can be used in fire alarm systems, but Class B Loops are the most common for non-addressable fire alarm loops.
You can see how the fire alarm system works by ordering the book "Make It Work - Conventional Fire Alarms
" by Douglas Krantz.