I have a QuestionDoug,
I'm a Sr. Maintenance tech at a large distribution center for a health company. At the moment our fire panel isn't being powered by direct electrical current due to a circuit breaker fail. We are running on two 12 V 8AH batts as a backup system. I realize the cells are 8 amp hours but do those amp hours start when the alarms go off or does the 8AH start as soon as I connect them to the panel? I'm wondering if I have to replace them every 8 hours or will they last longer without a load (sounders / strobes) on them.
Thanks, A W
Backup BatteriesThe batteries are 8 amp hour batteries. However, the 8 amp hours means how much electricity they have to give, not how long they will last.
Like an 8 ounce glass of water, 8 ounces is how much water is in the glass. If the water is just sipped, the water in the glass might last for many hours. However, if the person drinking is really thirsty, the water might last only minutes, or less.
Your fire alarm system probably sips the electricity so the batteries should last about 24 hours, but don't count on it.
Fire DetectionKeep in mind if it doesn't work, the panel doesn't cause a fire. It's just that if the primary AC power and the backup batteries quit, the panel is essentially dead and won't detect a fire. In other words, if there is a fire, no one will know about it until the fire is quite large.
Horns and StrobesThe horns and strobes only use electricity when there's a fire, so they should be left wired into the system.
Fire WalksWhen the panel quits working, that's when you need to use people to replace the panel's fire detection function. Someone or several people will have to walk through the whole place every half hour looking for possible fire.
Check with the fire marshal in your area about how the fire walks are supposed to be implemented, and to indicate what documentation is needed to show that the fire walks were performed.
Fix the BreakerFixing the breaker is the easy way to get the fire alarm system back to normal. It really is recommended that you get the failed breaker fixed right away, no waiting for estimates.
Thanks Doug, you basically confirmed exactly what I was thinking. My boss is not the most tech savvy guy, big surprise, so your answer to my question worked out great. I have our alarm company/electrician coming in today to get us back online. Hopefully no surprises, though, I'm sure you know how Fridays can be. Fingers crossed.
Thanks very much, A W
Why are Battery Date Codes so Cryptic? -- For safety reasons, the NFPA Code requires the replacement of fire alarm batteries within 5 years of manufacture...Read More
Do You Have to Replace Fire Alarm Batteries in Pairs? -- The question is asked: In a fire alarm system, where backup batteries are wired in series, can the batteries be changed out one at a time, or do the batteries have to be changed out in pairs? Remember that the... Read More
When Should Fire Alarm Batteries Be Replaced? -- The 2007 NFPA72 shows in Table 10.4.4, Item 6(d)(1), that the sealed lead-acid batteries used for battery backup in fire... Read More
Standby Batteries - Is there a reason why I shouldn't change them myself? -- I am OK with the cost per battery but I am having a little heartburn over paying someone $115 to do a simple replacement of the batteries. UNLESS I am missing a step that I am unaware of? I believe I need to notify our alarm company that I am changing batteries and to put us in test mode. Read More
Want New Articles
Twice a Month?
Join Short Circuit