J Wrote:Hi. Do the technicians have to reprogram the fire alarm system after relocating devices just a few inches from their original position? In this case two strobes are being relocated. One is moved to an adjacent wall and the other one is moved about 2 feet away.
Thanks in Advance
Douglas Krantz Wrote:If devices aren't moved to other circuits, if the room descriptions are not changed, if the wires land on the devices in the same place as they did before, for the panel there is nothing to change in the programming.
I assume that the strobes are tested by using input devices to put the panel into alarm to see what happens - make sure the strobes light during an alarm. If the whole system works as it is supposed to, and the panel doesn't show any trouble, no programming is needed.
Can Class A wiring be used for speaker circuits? -- Our client is insisting on Class A for the speaker circuits, instead of Class B... Read More
Can Two Different NAC Circuits be in the Same Conduit in Class A? -- Keep in mind that the purpose of Class A isn't so any problem with the wiring can be repaired in a timely manner; the purpose of Class A is to keep the system working once ... Read More
It's just one more strobe, what's the problem? -- Sometimes, after a building has been established for years, the fire marshal or the building owners want to add another horn or strobe. Or maybe, with remodeling, more horns and strobes are just added to an existing Notification Appliance Circuit (NAC). Really, it is just one more strobe and the circuit works... Read More
Can a Person Just Add a Horn or Strobe to an Existing Notification Appliance Circuit (NAC)? -- In a building that has been remodeled and remodeled, when a fire drill is sounded, have you ever found that a few strobes are running slow or won't even work? Then, when troubleshooting... Read More
Want New Articles
Twice a Month?
Join Short Circuit