I have a QuestionGood Day Sir:
Sir, I would like to know what type of signal is there between addressable fire detectors and the fire alarm monitoring panel.
Actually I want to know how the address / location of the sensor is transmitted to panel. How does the panel know which sensor is activated as there are lot of sensors in the zones.
Please reply my query & help me to improve on my knowledge.
Thanks in advance.
Best regards A A R M
Signaling Line Circuit (SLC)The Signaling Line Circuit or SLC in a fire alarm system is a power and computer style data bus. It is used to provide power to the computers inside each module and detector (each device), carry information from the panel to the devices, and carry information from each device to the panel.
Because this is a life-safety system, all power and communication has to be extremely reliable. In essence, the power for the devices and each signal sent take turns on the wires so there is no electronic confusion between the signals.
Addressing the DevicesThe panel has no idea where in the building the devices are located, and the devices don't know where they are either. The panel only calls out to the devices using the number programmed into each device (its address), and the devices respond when their number is called out by the panel.
I'm OKIt's an "I'm OK" system. The panel sends data out on the Signaling Line Circuit (SLC) and basically says "Number 27, are you there?" Module or Detector 27 had better answer back data saying "I'm here and I'm OK" or the panel assumes that device number 27 has a problem.
When device 27 doesn't answer, device 27 says there is some sort of trouble, or device 27 says there is an alarm, the panel looks up the location information on line 27 in a look-up table. At the time the fire alarm system was installed in the building, the look-up table in the fire alarm system's database was provided by the fire alarm installer.
The look-up table has lines in it that match the numbers assigned to the modules and detectors. Each line in the look-up table also has a sting of numbers and letters (characters).
Keep in mind, though, the panel isn't very smart; the panel doesn't know what this string of characters means.
The panel then displays the string of characters on its screen. It's up to the original installer to make sure the string of characters uses the words of the location.
Power and Computer Style Data Bus
Thank you for the clarification.
A A R M
How Does Multiplexing of the Signaling Line Circuit Work? -- Depending on what one needs to understand about a circuit, the circuit can be thought about in different ways. Take for instance a Signaling Line Circuit (SLC). A Signaling Line Circuit is a circuit that starts from the... Read More
NFPA's 7 Classes of Fire Alarm Paths -- The NFPA has divided the signal paths in a fire alarm system into 7 classifications: Class A, Class B, Class C, Class D, Class E, Class N, Class X. These classifications don't show how to wire up anything, these classifications show what happens when things go wrong... Read More
Just What Is a Signaling Line Circuit (SLC)? -- The SLC (Signaling Line Circuit) is another way of saying Data and Power Circuit. Along with added power to run the sub-computers and their input and output circuits, it's a computer data-buss ... Read More
Can an SLC loop (Signaling Line Circuit), whether Class B or A, also carry the power to activate (turn on) a horn strobe? -- The Signaling Line Circuit (SLC) is meant to carry signals between addressable devices (Modules and Detectors) and the panel. In some ways, the addressable devices can be thought of as extensions of the panel itself. The SLC can be thought of... Read More