Fire Alarm -- Description
Wired in either Class A or Class B configuration, in supervision
the fire alarm speaker is treated just as if it was any other fire alarm device. When active, the fire alarm speaker is treated as if it was any other public address sound distribution speaker.
Why Can't a 70 Volt Speaker be Used With a Fire Alarm System?
By Douglas Krantz
When the fire alarm system is active and is being used for EVAC or voice, there is no difference between the speaker audio used in voice EVAC and the speaker audio used in a distributed sound overhead paging system.
It's still the same 25 volt or 70 volt AC audio power sent out on a two wire sound system.
hen the system is not being used to send out audio, the fire alarm system is testing the building wiring using a direct current supervision
voltage. The difference is the paging system cannot handle this feature.
When the fire alarm system is being supervised, if a paging speaker is used on the system, the transformer in the paging speaker will short out the supervision voltage. The fire alarm speaker won't short the system.
The reason is inside the fire alarm speaker assembly. The assembly uses a Direct Current (DC) Blocking Capacitor to keep the DC supervision voltage out of the transformer.
Besides the DC Blocking Capacitor and other than being tested, approved, and listed by UL, CE, or some other testing agency, there is no difference between the regular overhead paging speaker and the fire alarm speaker.
Just remember though, even though it is meant for the same voltage audio system, don't use an overhead paging speaker on a fire alarm system. It will short out the supervision current
, and when a fire occurs, the fire alarm panel won't send EVAC audio down that Notification Appliance Circuit (NAC).
How Do I Shut Down Auditorium Sound on Fire Alarm?
-- I have an auditorium that needs to have the sound shut down when the fire alarm is activated. The sound board or DSP (Digital Signal Processing) has an emergency input that I can connect to, but the prints are engineered to use the SLC loop to shut it down ... Read More